Answers were Sorted based on User's Feedback
Answer / syed shahid
The steam pressure in the last stage of the steam turbine
is very low after performing the work. To make the steam
flow to the condenser to convert into condensate
(liquid/water)it is necessary that the pressure be much
lower in the condenser to make the steam flow to the
condenser.Therefore, vacuum is maintained in the condenser
using either vacuum pump or steam ejector.
|Is This Answer Correct ?||75 Yes||7 No|
Answer / sethu
How vacuum is created?
Basic vacuum created in the LPT exhaust side is because of condensing process. Phase change is occurring at the exhaust side i.e. conversion of steam into water. Specific volume of water is much lower than the steam.Hence when the condensing process happens, volume of steam reduces and basic vacuum is created.
Apart from this, vacuum pumps are provided to remove non condensable gases/air ingress which reduces heat transfer effectiveness.
Why vacuum is created?
To improve LPT cylinder efficiency & thus the load/work done shall be improved.
Effect of over vacuum?
It causes sub-cooling effect where hot well temperature reduces more than design which required to be added in boiler leads to heat loss. Also flow accelerated erosion in LPT last stages.
Effect of under vacuum?
LPT efficiency reduction which causes lesser work done & leads to reduced load output.
|Is This Answer Correct ?||48 Yes||4 No|
Answer / jahanzaib
If we answer it in simole way then we just answer that to
avoid back pressure on steam turbine we maintain vacuum in
condensor......(This is the answer Why we create vacuum in
Second question some one ask what happend if vacuum loss
occure in condensor then we explain that
.)work done by steam turbine will reduced that will
eltimately reduce the effency of steam turbine.
.)LP turbine side temperature will start risisng casuning
damage to LP side turbine blades.
|Is This Answer Correct ?||10 Yes||3 No|
Answer / rajkumar
vacumm is only maintaining for rising the turbine workdone,
how means it will reduce turbine outlet temperature due to
long time expansion wih out condensation of steam on last
turbine stages corresponding to the vaccum pressure,
that means max heat will be recoverd on turbine,
and also already temp less of turbine exhaust so condensor
cooling water flow also needed less
|Is This Answer Correct ?||18 Yes||12 No|
Answer / jk gangwar
Its main purposes remove for non condense gas's in steam. If here is not vaccum then may be steam condensate drops collected on turbine blades and can damage turbine blades and turbine casing. Overall turbine work efficiency will increase if vaccum apply in surface condenser. In Common case we use Steam injector's in series with primary and secondary injector's and condenser.
|Is This Answer Correct ?||7 Yes||2 No|
Answer / anirban
Vacuum is created in condenser due to regular flow of steam in turbine nd create it's condensate.as much lower the pressure is it helps to built more condensate by using ejectors or hogger
|Is This Answer Correct ?||2 Yes||0 No|
Answer / c.reddi sankara
Sudden expansion of steam in the condenser space which is higher enough to drop the pressure below then atmospheric pressure is the cause to create negative pressure or vacuum.(And air pumps are also used to create vacuum).
As we know any gas will expand and cooled immediately in vacuum due to negative pressure.
Hence when the pressured steam expanded suddenly in in vacuum and cooled then the cycle efficiency will increases.
|Is This Answer Correct ?||1 Yes||0 No|
Answer / venkatesh
Vacuum is created in condensor because in LPT turbine steam having less pressure after expansion so we need that steam to convert into water.So at 1 atm and 100 deg water will convert into steam.At lower temp we need to convert steam in to water so we used vacuum pump to create negative pressure.if we achived Ideally -1 vacuum then their is no loss of water but practically it is not possible max we can reach -0.9 vacuum.
concl:Vaccum is needed to convert low temp stm into water.
|Is This Answer Correct ?||5 Yes||5 No|
Answer / ragi sunil chowdary
so if we
dif wil b
If dere is
|Is This Answer Correct ?||3 Yes||4 No|
Answer / abdul aleem shaik
if the vaccum is not created in the condensor then how the steam will flow from turbine to the condensor.......???
ok let me explain.....
the pressure of the exhaust steam will be very low, so to make the steam flow through the condensor we should maintain vaccum in the condensor.......
if u didnt understand ask again i will explain
|Is This Answer Correct ?||24 Yes||26 No|
to improve the existing power factor whether capacitors have to be added in series or parallel.and why
why ceiling fan give hising sound
maximum transmission voltage in india ? & where is it situated ?
How to calculate impedance volt in Transformer?
What should be the Sandwitch type Al. bus bar capacity for 2 M.W.Gen. set, having continuous full load current- 3463 Amps,ambient temp.- 50 Deg. C., Required temp. raise-20 deg.C., it will run 24 hrs, 365 days on full load, required highly reliable.
when a motor is connected in parallel with the existing motor the pf will change or not?
hi frnds.....anyone get any reply from HPCL. I HAVN'T.....B,COS written will b on FEB 17 th.
Why PT voltages are measured with respect to ground? What do u mean by voltage or current polarized.
Calculate torque developed by the 3-phase, 5 H.P., 4 pole induction motor runs at 1500 rpm A 23 N-m B 21 N-m C 10 N-m D 0 N-m
in domestic service connection,what is service main?
Can we convert off load tap changer transformer to on load tap changer transformer
how can i design a APFCR panel? please explain with example..