why drum level is increased when one of the running coal
elevations are suddenly tripped?
Answers were Sorted based on User's Feedback
Answer / g.l.nepalia
The evaporation rate of water in drum reduces whereas feed rate of water in drum remain unchanged
|Is This Answer Correct ?||30 Yes||4 No|
Answer / ns satyaraj
when any coal elevation trips ,heat input to boiler reduces, so evaporation rate reduces and steam pressure reduces and water feed remains same ,so drum level increases
|Is This Answer Correct ?||3 Yes||0 No|
Answer / ril
feed water remain unchanged incase of cascade system if it is in single element drum level will be unchanged
|Is This Answer Correct ?||2 Yes||3 No|
Why attemperation is required in HRSG in a combined cycle power plant?
During shutdown of Steam Turbine,How do we cross the critical speed?
Why reheater is not used after IP turbine.
What is droop.
our 125 kva DG does not start in AUTO mode works normally in MANUAL mode please give me a solution.....
im try to calculating seawater flow required for SW-FGD system. I need a guide, equation or method to do it, can some one help me! Thanks very much
why do we use contro fluid tank (cft)in turbo generator area(tg) in power plant?
why we use reduction gear box to reduce turbine high rpm to 1500 rpm in small plant
We have Demin Closed cooling water system with expansion tank for cooling oil system. Expansion tank having N2 bladder. Whenever N2 bladder bursts out, Closed cooling water circuit pressure drops and make-up happening, eventhough there is no leaks. And how Circuit pressure drops?
what is turn down ratio
what is the defenation of efficiency in the high pressor boiler? what is the formila of efficiency in the high pressor boiler?
why Subcritical has 60% condenser capacity