How to Calculate the maximum Demand required for a
connected load for a manufacturing Plant
Answers were Sorted based on User's Feedback
Answer / mior
First of all, you need to know your total connected load
(TCL). Then, you apply Diversity Factor at your TCL to get
the Maximum Demand (MD).
You have 1no. 36W Florescent Lighting and 1no. socket outlet
(250W). Your TCL will be (36W + 250W) = 286W.
In actual, the TCL may only contribute certain percentage
for your MD; that's why you need to apply Diversity Factor
Common practice, light fitting will contribute 80% and
socket outlet giving 40% for your total MD.
Hence, your total MD will be = [(36W * 80%)+(250W*40%)
Therefore, your total MD to be declared for your Utility
Provider will be 128.8W.
The link below might help your for more info.
|Is This Answer Correct ?||66 Yes||9 No|
Answer / yogish
There is no specific method to calculate the MD from the
CL. It really depends on the following: -
1. Type of industry: Continuous or Batch process, Heavy or
Medium or Small
2. Mechanical load or Heating load or Furnace load
3. Plant at infant stage or stabilised
4. Standby loads included
5. Largest single load and its starting method
6. Possibility of staggering load without affecting
7. Whether the major motors are optimally sized or oversized
We can get at some figure, only by experience in a similar
|Is This Answer Correct ?||38 Yes||24 No|
Answer / sachin
First try to know what is mean by max demand . Max demamd
is the simutaneous max requirment of power for any unit.
there is no standard practise to calculate the MD of any
unit . but one can carry out as follows.
1] CALCULATE THE TOTAL CONNECTED LOAD .
2] APPLY DIVERSITY FACTOR - IT IS THE PART OF EXPERIENCE
AND MAY VARY FROM UNIT TO UNIT .
3] TOTAL CONNECTED LOAD X DIVERSITY FACTOR = MAX DEMAND
|Is This Answer Correct ?||21 Yes||7 No|
Answer / parag nikumbh
MD in KVA = (connected load in kw x Diversity factor) / P.F.
Diversity factor can be calculated as Running load/Installed load
|Is This Answer Correct ?||14 Yes||4 No|
Answer / j manikanta
Can you clarify my doubt.
we have a Total connected load 100 KW. We want to take an HT Connection in Andhra pradesh. So how much KVA will be sufficient for my plant. Kindly suggest me about CMD.
We will use 80-90% of Connected load. And what is diversity factor. how we need to calculate this
|Is This Answer Correct ?||1 Yes||1 No|
Answer / kanand078
first calculate the total load in plant. and find the
voltage and current,after u can use this formula and
calculate the MD=V*I
|Is This Answer Correct ?||23 Yes||59 No|
what is LT & HT?
why we did not get shock by touching +ve OR -ve busbar (Which are going to supply cell voltage) of Rectifier- Tranformer in electrolysis plant?
What is the de rating factor of cable? What is the importance of the de rating factor in cable select
Whta is WT in a transformer, specify its function.
what happens to current , when voltage drops .?
why transformers are put with supply for 24 hours before giving supplying to a locality?
hey guys i scored 910 on GRE and 67 on TOEFL respectively.I have an aggregate of about 74%in my B tech.For which colleges should i apply for an MS program in electrical engineering.I am looking for colleges in NJ,SC,NC,GEORGIA, NY. Please reply with a good response.....
what will be happen if earth point is being used for as a neutral point for raw power , and same will be used for ups earthing
How will polarity test of Dy5 transformer ?
I have a generator of 300kw.400V,50hz . what is means can i assume the load Red Phase with Neutral 300kw.Yellow phase with neutral 300kw and Blue with neutral also 300Kw. or - red with neutral 100kw same as yelloe and blue phase also giving 100kw with neutral respectively
if we connect a ohmmeter across shorted capacitor .what will be the reading..will it be zero or infinity
which model T or pie model is prefarable in power syatem